TRS-B series AC surge protector (hereinafter referred to as SPD) are suitable for AC 50/60HZ, rated voltage up
to 380v LT、TT、TN-C、TN-S、TN-C-S and other power supply system, it protect to indirect and direct lighting effect
or other transient over voltage
SPD design according with GB18802.1/IEC61643-1 standard.
Structure and principle
SPD is a port ,shocking protection, indoor –mounted installation and voltage limited.
SPD hold disconnector inside, then SPD breakdown failure by over heating,the disconnector can remove form the
power grid automatically, and show indication signal, when SPD is working normally, visible window display green , lt
display red when it breakdown and disconnect.
1P+N ,2P+N ,3P+N spd consist of 1P ,2P ,3P SPD + NPE zero protection module , apply to TN-S、 TN-C-S and
other power supply system
With 35mm standard DIN-rail mounting, connecting copper stranded conductor is 2.5~35 mm².
At front of SPD each pole must be setted protection ---used fuse or miniature circuit breaker lightning current SPD
protection ,after SPD breakdown to short circuit protection.
SPD install on protected line (equipment) to the front and c onnected to supply line. A class products install in the
building home-entry line hold large surge current total distribution box.B,C class products most install on the floor distribution
box ,D class products close to the front – end equipment that smaller surge current, smaller residual voltage place